02004nas a2200157 4500008004100000245015700041210006900198260002500267520129500292100002001587700001601607700002101623700001901644700001801663856016501681 2018 eng d00aOpenBuildingControl: Modeling Feedback Control as a Step Towards Formal Design, Specification, Deployment and Verification of Building Control Sequences0 aOpenBuildingControl Modeling Feedback Control as a Step Towards  aChicago, ILc09/20183 a

This paper presents ongoing work to develop tools and a process that will allow building designers to instantiate control sequences, configure them for their project, assess their performance in closed loop building energy simulation, and then export these sequences (i) for the control provider to bid on the project and to implement the sequences through machine-to-machine translation, and (ii) for the commissioning agent to verify their correct implementation.

The paper reports on the following: (i) The specification of a Control Description Language, (ii) its use to implement a subset of the ASHRAE Guideline 36 sequences, released as part of the Modelica Buildings library, (iii) its use in annual closed-loop simulations of a variable air- volume flow system, and (iv) lessons learned regarding simulation of closed-loop control.

In our case study, the Guideline 36 sequences yield 30% lower annual site HYAC energy use, under comparable comfort, than sequences published earlier by ASHRAE. The 30% differences in annual HYAC energy consumption due to changes in the control sequences raises the question of whether the idealization of control sequences that is common practice in today's building energy simulation leads to trustworthy energy use predictions.

1 aWetter, Michael1 aHu, Jianjun1 aGrahovac, Milica1 aEubanks, Brent1 aHaves, Philip uhttps://www.ashrae.org/File%20Library/Conferences/Specialty%20Conferences/2018%20Building%20Performance%20Analysis%20Conference%20and%20SimBuild/Papers/C107.pdf